# Infinite Generator

I'm setting up a case representing an infinite generator. I assume modeling this dynamically is just as simple as having a large inertia and large damping coefficient for said generator?

Thanks

First time here? We are a friendly community of Power Systems Engineers. Check out the FAQ!

I'm setting up a case representing an infinite generator. I assume modeling this dynamically is just as simple as having a large inertia and large damping coefficient for said generator?

Thanks

3

Use the classic model GENCLS, and no exciter,nor governor models. In the base case, give a large MVA to this machine and set its Xs = 0.01 or less.

0

I have done same .. On tripping one of generator ... Initially, my infinite generator is picking up the load, however, later , that additional load is being distributed on all of remaining generators and infinite generator is going back at its initial load... whereas, I want to have that infinite generator to keep serving that deficit..

I wanted to attach the Pelectrical images for your reference.. however, website is denying by saying to "not have Karma>10"...

What is the purpose of this Xsource = 0.01 ? What is the relation between the modeling Infinite Bus and the Xsorce parameter ?

jesus...is no one else running into this problem?!?!?

0

The short circuit power in MVA for the "infinite bus" is determined by Mbase/Zsorce. Select GENCLS with H=0 to make the generator infinitely heavy in the dynamics (infinite inertia and constant frequency)

0

I decided to post in here because my question is relevant: "How do I model an infinite bus?" To be more exact, I need to model many infinite buses so "How do I model a number of infinite buses in a case?" I am asking in both load flow network data and dynamic model terms.

- What bus type do they need to be? Generator buses or Swing buses?
- Voltage schedules need to be set to 1, right?
- H (inertia) and D (damping) in Dynamic Data have to be 0, both of them ?
- No controls, no governors, no nothing?
- Generator model is GENCLS, right?

Asked: **
2015-10-05 21:02:21 -0500
**

Seen: **3,766 times**

Last updated: **Sep 26 '16**

exporting dynamic simulation results to excel using python

Python API to Terminate Dynamic Simulation

How to change the time step of a dynamic simulation case ?

create dynamic data for a PSSE network file

How to ramp the value of exciter output voltage in dynamic simulation?

API for changing tap position in dynamic simulation

Generator Modulation During Dynamic Simulation

run dynamic simulation without having dynamic parameters in the *.dyr file

whit loves you. Content on this site is licensed under a Creative Commons Attribution Share Alike 3.0 license.

Thanks jconto, the damping and inertia coefficients should be large though correct?

Yes, that is correct.