# How does psse calculate frequency at bus?

I see that psse outputs the frequency at bus with BUS*FREQUENCY*CHANNEL. But how does it do the calculation?

Thanks

First time here? We are a friendly community of Power Systems Engineers. Check out the FAQ!

I see that psse outputs the frequency at bus with BUS*FREQUENCY*CHANNEL. But how does it do the calculation?

Thanks

add a comment

0

Hello guys, thank you for your responses. So PSSE uses the derivative and washout filter for the bus calculations?

The Program Application Guide gives insight about the process of dynamic calculation but not about the method of frequency calculation at buses. Do you know where can I check this? Thanks

0

To complete the previous answer, I have also realized that pss/e uses a 3rd order median filter, after doing the derivative. the output of the median filter then goes to a low path filter, with time constant of Tf, defined as Dynamic solution parameter.

0

The bus frequency is calculated from the change in bus voltage angle. A filter is applied to smooth the frequency result, using a 0.04 s time constant for the filter. The frequency filter time can be changed in "Dynamic Solution Parameters".

Asked: **
2018-11-05 17:29:16 -0500
**

Seen: **169 times**

Last updated: **Nov 09 '18**

Generator Modulation During Dynamic Simulation

What are the factor we should consider while modeling the wind farm?

API for changing tap position in dynamic simulation

Send data to Excel whit NaN values

How to write a user-defined model

dynamic simulation with load change

How to retrieve faulted current from Bus to Dummy Bus

How to do dynamic simulation to test the transient stability of power system?

whit loves you. Content on this site is licensed under a Creative Commons Attribution Share Alike 3.0 license.